Interval metering data, weather station data
Visualization of gas consumption over three years (x-axis) through the 24 hours in a day (y-axis). Savings opportunity is indicated by excessive gas use at night, shown in orange and red on the left. Reduction of red to limited hours on the right shows that some waste has been eliminated. Regularly reviewing this visualization helps maintain the improvement over time. Aligned with the heat map data, and below it, a chart displays daily heating degree days and cooling degree days at the weather station associated with the selected meter.
Zone temperature data, systems analysis, patterns for augmented intelligence
Calculated data for analysis of zone reheat issues
Campus-wide data display of selected measurement for all air handling units
Behavioral system optimization, fume hood sash heights
Correction of a fault does not need to be automated; visualization of some data can influence occupant behavior. Here, fume hood sash heights are calculated using fume hood exhaust airflow station measurements, fume hood face velocity measurements and fume hood equipment metadata (sash width). The visualization makes it obvious when a sash is left partially or fully open for a long time. Giving occupants access to this data can help them better manage their usage of fume hoods.